The causes of vibration in the deaerator are:
1.In the process of charging the deaerator, improper heating causes uneven expansion or uneven distribution of steam and water loads.
2.The amount of water entering the deaerator is too large, and the pipe vibrates to cause the deaerator to vibrate.
3.The internal parts fall off during operation.
4. Suddenly entering cold water during operation makes the temperature of the water tank uneven and causes shock and vibration.
6.The deaerator pressure drops too quickly, soda-water co-transpiration occurs.